The L’OREAL is trying to give clean and healthy environment from the Production activities to act in a responsible and environmentally sustainable manner in our business. We are tried to contribute in global effort of the environment and always improving Environmental Management System. This means we must meet all the requirements for the safe discharge of our wastewater effluents and in strict and accordance with all other legal requirements. This wastewater treatment activity is important to the L'OREAL group because in the event of a malfunction or breakdown, to avoid any pollution and any risk of damaging the groups image.
Complete Design, Engineering done by M/s AQUCARE SOLUTION ENVIRO ENGINEERS. Electro Mechanical Supply has been done from INDIA. Installation, Commissioning & PG Test with operation training successfully completed by ASEE Team at L'Oréal Kenya
In 2016 L'Oréal Kenya awarded turnkey 80 KLD ETP project to M/s Aquacare Solution Enviro Engineers. Which is successfully completed within 4 months of time duration in 2017 The plant is running with designed capacity and desired output water quality meeting all local norms for last 5 years. Which is great achievement and reference.
DESIGN & ACHIEVED WATER QUALITY
|Parameter||Unit||Raw Effluent||Design Treated Water Quality||Avg.Achieved Treated Water Quality|
|Flow||m3/day||40 - 50||50||50|
|pH||5.5 to 7.5||6 to 8.5||7.5|
|Total Suspended Solids||mg/lit.||3000||<20||<~5|
|COD||mg/lit.||8,000 - 22000||<50||<~20|
|BOD ( 3 days at 27oC )||mg/lit.||1000 - 3000||<30||<~10|
|Oil & Grease||mg/lit.||500 – 1600||<10||<~5|
Your email address will not be published. Required fields are marked *
We're here to help and answer any question you might have. We look forward to hearing from you..